Plane crashes rarely happen, but the fear of an accident is real for many people. Still, thousands of Americans fly every day. The NBC television drama “This is Us” showed that Crock-Pots can cause house fires, but we’re still cooking chilis and roasts while we’re away at work.
The threat of energy storage systems causing or contributing to building fires is also real yet incredibly rare, but as adoption grows, life and property wellbeing will become larger concerns.
Right now, solar + storage fire worries usually arise around lithium-ion technologies, with a divided war between nickel manganese cobalt (NMC) providers (Tesla Powerwall, LG Chem) and those developing lithium-iron phosphate (LFP) batteries (sonnen, SimpliPhi). On paper, NMC batteries have an increased risk of thermal runaway, the phenomenon that causes battery fires, simply because of the addition of cobalt. But put even an LFP battery in a less-than-ideal situation, and the end result of an accidental fire is the same — potential damage to the system, nearby surroundings and human life.
“Just because the likelihood is different doesn’t mean the impact is different,” said Victoria Carey, senior consultant of energy storage for quality assurance company DNV GL. “When doing installation design, you have to design for minimizing the likelihood [of a fire]. It’s always good to look at the chemistry capabilities and balance how to mitigate the impact with whether that battery’s energy density is exactly what’s needed for a particular application.”
Batteries that like cool, constant temperatures probably shouldn’t be installed outdoors in the desert. Off-grid winter cabins might benefit from using lead-acid batteries over the latest lithium product. Just because a solar installer is a certified dealer of a specific battery chemistry doesn’t mean it’s the best product for every job. Carey said she is comforted that the solar industry is taking battery installation more seriously now than even two years ago.
“Folks have been treating batteries as a black box add-on to their equipment they’re installing. There’s now a realization that although there are no literal moving parts, there’s a lot of different small components that need to be managed and are delicate,” she said. “There’s a sort of awakening in the last year. We’ve called energy storage the ‘Wild West,’ and it is certainly still in early development stages, but there’s a sheriff in town now.”
Although battery fires aren’t likely to happen, it’s still important to design and plan for the worst.
What causes battery fires?
If a battery is going to catch fire, the likely cause is thermal runaway. This is when a battery experiences an increase in temperature that eventually leads to cell short-circuiting or disintegration that can spark a fire.
There are three main abuse factors that can send a battery into thermal runaway — mechanical, thermal or electrical. Mechanical would be physically damaging the unit, which can generate gases or increase the heat of a battery cell. Thermal is heat-related — air conditioning or airflow not reaching the cells, allowing heat to build up. Electrical abuse happens during overcharging, undercharging or shorts from the inverter. Often, damage can be reversed if caught quickly.
“There is an opportunity once that abuse factor has been put onto the cells, if it’s removed then the thermal runaway condition may not occur, but there is a point of no return,” Carey said. “If it’s not stopped, it will continue through these second-order effects, which at its core is a release of potentially flammable gases. If there’s an ignition source, that can then become a fire. If there’s not an ignition source, these seminal gases can gather in large enough volumes that could result in explosive conditions.”
DNV GL is trying to understand the risks with battery fires before they happen. It released its first Battery Performance Scorecard in 2018, which ranks and evaluates different types of batteries based on performance and safety testing. By putting the batteries through the wringer, DNV GL finds the performance limits of the systems or can produce thermal runaway, depending on the test.
“The whole goal of destructive testing is to determine if something goes into thermal runaway, what happens?” Carey said. “Yes, there may be some batteries that are more resistant to thermal runaway, but we have found across the board that they release the same chemicals with the same level of toxicity and potential flammability.”
A safe battery is determined by its initial manufacturing. DNV GL hopes its battery scorecard brings more transparency to the market.
“There’s a resistance for companies to share even their name that they’ve participated in this type of testing. There’s concern about how it will be perceived by customers,” Carey said. “Creating greater transparency in the market is one of the things that we see is really important to improving quality of the systems.”
How should batteries be installed to prevent fires?
If battery installers follow the manufacturer’s manual and adhere to the locality’s fire codes and standards, the chance of a fire starting is near zero. LFP battery manufacturer Blue Planet Energy claims to make the safest lithium battery on the market for energy storage applications because of additional built-in safety links, but still, head of sales Gregg Murphy said the surest way to prevent battery fires is to install the system correctly.
“Any technology, if installed incorrectly, is a potential electrical hazard,” he said. “The biggest support in the market place is for installers to closely follow the installation manual on top of selecting safer battery chemistries. The top questions we receive in customer service are around installation best practices.”
Following best practices and using a little common sense goes a long way, said Brian O’Connor, fire protection engineer with the National Fire Protection Association (NFPA), which released its standard for the installation of non-residential stationary energy storage systems (NFPA 855) in September 2019.
NFPA 855 provides battery installation requirements that best prevent loss of life and property — the goal of all NFPA codes. O’Connor said some best large-scale storage installation practices include providing enough space between units for adequate airflow and fire breaks and having an appropriate fire suppression system on-site.
“We suggest to space batteries out in the building. If there are fire breaks between each, then the fire cannot escape one rack. If you can contain the fire to a smaller spot, it’s going to burn for a shorter duration, and you can limit the damage,” he said. “Another suggestion is installing a sprinkler system. Lithium-ion batteries do not react to water, so you can put a lot of water on them to cool them. It won’t extinguish the fire, but it will stop the fire from spreading and jumping to other exposures.”
O’Connor said many of NFPA’s large-scale battery installation requirements can be translated over to the residential market with an extra dose of practicality.
“We use more common sense and basic rules for residential batteries because it’s difficult to enforce all these details. No one is going door to door to see,” he said. “If you’re going to install a storage system in the garage, make sure you have space for vehicle protection — if you’re backing into the garage, you don’t want to hit the battery. Make sure batteries are not in the place you sleep, because it would limit the time you egress your house. Don’t install a battery outside under a window, because during a fire, windows are used to exit the house.”
While the likelihood of a fire in a residential application is lower, installers should still plan for accidents. Installing batteries in rooms with fire-rated walls without a lot of clutter that could impede airflow is a basic first step. Keeping batteries away from livable spaces (bedrooms, living rooms) allow for better survival rates in case a fire does happen. So, all those battery company promotion pictures showing systems in the living room as aesthetic focal points — no way. Keep the battery in a garage or unoccupied utility space, just to be on the safe side.
What are some best operating practices to prevent battery fires?
A little common sense follows to the operational side of an energy storage system. A high-functioning battery management system (BMS), which typically comes standard with lithium-ion battery systems, will help to balance charging and discharging rates, monitor battery voltage and measure temperature to ensure the system doesn’t run into problems. But just because a BMS is monitoring the battery’s health doesn’t mean the operator should push it to its limits.
“The critical part is making sure that whatever the battery was designed to do and whatever the BMS is designed to protect is what that battery is being used for,” Carey said.
O’Connor’s best advice is to prepare and plan for the worst — know what to do in case of a fire and coordinate with first responders. NFPA 855 requires safety labels explaining what type of battery is installed and if there is a suppression system in place. These precautions are very important to first responders so they aren’t surprised when they arrive at an emergency.
“A big concern is stranded energy. You can’t discharge these batteries quickly when they’re on fire,” O’Connor said. “Even when a first responder is doing cleanup, there is a shock potential. If they put [an axe] into a battery that is energized, there is potential for injury. So labeling is important.”
Above all, just be smart about installing, operating and owning an energy storage system. When we fly on airplanes, we have access to safety information and receive demonstrations on what to do in an emergency. An accident isn’t likely to happen, but it’s good to have that information on-hand, just in case.
“Operationally, as long as these systems follow good quality practices, you have a very low likelihood of failure,” Carey said. “But if you don’t admit there could be a failure, you’re not going to prepare the people who are trying to save lives and property appropriately. It’s a touchy subject to say your product can fail, but I think it’s incumbent upon people to act responsibly and admit that something could happen.”
Chris Newton says
What happens if my lithium battery was partly submerged in water during a flood?
A. Nilssen says
I am trying to learn as much as I can about home backup systems. It is very hard to find a company that actually understands the whole installation process and any dangers associated with the lithium batteries. Thanks so much for this info.
If anyone has used a reputable company in Southern California area, please let me know…..
Hello, I have read a lot recently about Vanadium Redox Flow Batteries. Apparently they do not catch fire (primarily because they consist mainly of water), they do not degrade like lithium batteries so potentially last forever, and they are 100% recyclable because all the vanadium in solution can be recovered and used again.
Anthony Davis says
Under certain confirmations like fire, L-Ion solar batteries can discharge a gas, Hydrogen fluoride which is poisonous to humans.
Is this true and is it unlikely ever to occur and how would such a problem be tackled by the fire brigade, should they have specialised training before such an event occurs ? Thank you.
I had a battery fire recently with my solar system. It was on a west wall in L.A. Anyone have expertise SoCal who can set up a new, safer inverter and storage system?
Nigel S says
Firstly well done for tackling a real issue in the market.
However you say the risk of Fire is incredibly rare, on what basis is that statement made ?
There are a number of reported major fires in BESS systems, South Korea in particular has had multiple losses. Plus the fact that thermal runaway means that any small fire quickly escalates to a major loss and there isnt a clear system of controlling fires of this nature. It feels very much like the technology for storage is powering ahead but the control of the risk presented is not being addressed at the same time.
David Garrett says
What happens in a house fire situation?
What are the best fire fire fighting methods for Lithium Ion battery storage systems?
Deluge system on powerwall?
Lots of water or Dry chem?
How do you put the fire out if system is still energised with electrical energy?
Safety data sheet fire fighting information varies according to supplier and the message is not consistent across suppliers.
Fire Service was not helpful.
peter taylor says
Passive fire suppression system idea – I am not an expert by any means, however, if you have your whole house battery bank contained and ventilated, then on the top of the container, have a bin of fine play sand , separated by a fabric on a expanded (perforated) steel sheet, that if there is a fire, the fabric will burn/disintegrate, therefore releasing the sand and smothering the fire.
Rao Konidena says
Thank you for writing about fires in storage systems. Yes, it is possible. But, with new safety standards and proper installation procedures – the industry need not worry. I also like how you have initially framed the article. Yes, it is possible for accidents to happen. That is why they are called “accidents”. But just because accidents happen, does not mean we simply stop driving as an example.
George J Kamburoff says
I have had household batteries and two electric cars for years. I am not worried.
Greg Smith says
This is the Catch-22. California is adopting restrictions on ESS inside any part of the home including the garage. So, my garage-installed 10 kWh LFP battery system is too risky, but my dream EV Rivian, with a battery size of 180 kWh (18x), is perfectly ok to sit in my garage. Stationary ESS are now becoming victims of the same asinine mindset that brought us rapid shutdown.
Bruce Verhei says
I think eventually we’ll see a small room built with 5/8” Type X drywall, with vent high and low, like a gas appliance, except to allow heat to leave. A single fire sprinkler head will be more than adequate to stop fire spread outside the glorified closet.
For the non-fire protection people: Sprinkler seldom have false operation, if isolated from freeze. A sprinkler temperature rating should be 50f or greater, above highest temperature experienced in room.
Fire protection people: In a little room temperature at the ceiling rises much faster. Instead of standard 165f head, maybe an intermediate, 212f head would be appropriate. It won’t operate more than a few seconds slower in this fire situation.
Hi lots of good info about batteries , thanks for the heads up
“On paper, NMC batteries have an increased risk of thermal runaway, the phenomenon that causes battery fires, simply because of the addition of cobalt. But put even an LFP battery in a less-than-ideal situation, and the end result of an accidental fire is the same — potential damage to the system, nearby surroundings and human life.”
The bottom line is “best practices” in the installation and use of the product. A lot of batteries and probably most of the lithium ion technology in use today have electrolytes that are volatile liquids, the battery chemistry NMC, LiFePO4, or even less reactive chemistries like (LTO) can burn. As in the Surprise energy storage system in Arizona that burned last year. Utility Dive had an article out a few months back that ‘finally’ made some of the investigation findings public. This site had telemetry on the energy cargo system, monitoring conditions and operations. The energy storage container had air conditioning for temperature control and a fire suppression system on board. Now let’s talk about “best practices”. The fire was reported by a citizen driving by the facility and saw smoke. Emergency services called the fire department. Apparently the fire department wasn’t (fully) aware of the situation and attempted to stab an air sample from the container’s interior for toxic fumes. When the container’s door was cracked to get that air sample, it created an inrush of fresh air, a back draught and the volatile chemicals from the burning battery pack exploded. In this particular case, IF the energy storage container had been designed to vent each of the battery packs to outside air, this may never have happened. Now that this is known, it is possible to redesign the fire suppression system, vent each battery pack to outside air, incorporate emergency disconnects to each battery pack in the energy storage stack, have the fire department and all other emergency responders up on what the dangers are and have more telemetry function and alarm access information for the first responders to help determine a course of action.
NEMA 3R divided cabinet enclosures to hold all battery, charging, inverter and interface electronics, BMS would make a neat, functional space for the energy storage to be housed.
Juan LeonGuerrero says
Solarman, you sound like you took Communication Electronics training in the military, nice info. To Kelly Pickerel; You have us great information. How much, what kind and how long is the training the installers get. Do they get tested for knowledge and proficiency in all the areas involved with the system from solar cell to ground? I receive the same words by so many sales reps and techs, that the batteries are not dangerous.